2000 Litre Tankmasta Slimline Water Tank
Dimensions: 2350L x 650W x 2000H
Viscount Rotational Mouldings Pty Ltd (VRM) has been providing product solutions to the Australian market for over 25 years. Specializing in the rotational and injection moulding processes, the Viscount group forms part of the global Linpac network with operations in the UK, USA, Europe and Australia. VRM itself has manufacturing facilities in Carrum Downs, Victoria.
Slimline tanks provide the perfect solution when space is at a premium. The slimline tanks can be installed in areas that cannot be accessed by regular tanks. The TANKMASTA Slim is an easy and flexible system
|Dimensions (mm)||2350L x 650W x 2000H|
|Supplied Accessories||300mm Inlet Strainer, 90mm Overflow at 12 o ‘clock, 25mm ball valve|
|Fittings||1 x 25mm brass outlet|
|Water Tank Colour||Armour Grey, Black / Night Sky, Heritage Green / Cottage Green, Heritage Red / Manor Red, Jasper, Merino / Paperbark, Monument, Mountain Blue / Deep Ocean, Rivergum / Wilderness, Slate Grey / Woodland Grey, Wheat|
|Warranty||10 Years Manufacturers Warranty|
Slimline Water Tank Install preparation is essential to ensure a long and trouble-free life for your water tank.
A. Tank must be installed on a smooth, level reinforced concrete base. The base must be a minimum 100mm thick, 100mm longer and wider than diameter of tank. Remove sharp objects that may damage base of tank. Ensure that the soil base is suitably compacted before pouring the concrete.
B. Slimline tank must be installed adjacent to wall with 50mm clearance off wall. TANK MUST Not to be fixed to wall. MUST be freestanding. The tank should be placed in a position where it will not be subjected to heavy bumps or knocks.
C. Plumb from your down pipe using a First Flush Diverter / Leaf-eater “This should be used to remove any solids washed from your gutter that could contaminate your tank water” Then from the first flush into the top of the tank through the sunlight cover and into the tank bucket filter.
D. At the base of the rainwater tank screw in the correct size ball valve using Teflon plumbers tape to seal the thread. Connect your pump up to the ball valve on the tank using a minimum of 30cm of flexible suction hose and fittings. The flexible hose allows for expansion and contraction as the tank fills and empties.
E. Again using 90mm PVC pipe and bends, run from the rainwater tank overflow point down into the stormwater system where the old downpipe used to be connected. This may need to be altered to accommodate the 90mm round PVC pipe.